M90SE Striped Pipes
Black Couplers / EF / PN10 / SDR17
PE to Cast Iron P-Trap
Transitions and Adapters
Polyethylene 'Transition' or 'Adapter' fittings are used to connect PE gravity drainage pipe to another pipe material, such as: Ductile or Cast Iron, PVC, VCP (Clay), RCP (Reinforced concrete pipe). Transitions are typically a PE socket end with a rubber ring joint slides over the other pipes spigot end.
Manufacture - Transitions are machined from a single piece of PE100 PE hollow bar and include an integrated puddle flange. The puddle (when encased in Concrete) anchors the transition joint to the existing pipe material. This prevents changes in temperature and ground movement pulling the PE and transition RRJ socket off the existing pipe end. (Understand why PE pipes must be anchored here.)
Concentric vs. Eccentric Transitions - The difference in Inside diameters between the existing pipe and the PE pipe determines if the transition design must be Concentric or Eccentric. DSD states that Eccentric designs must be used where the internal diameters between the PE and joining pipe differ by ≥ 5%. This maintains a free draining level invert inside the pipe, avoiding an internal steps that cause septic pooling. Refer DSD PS Appendix 5A, Clause 5.8.9.
DSD PS Appendix 5A
Non Pressure use only - Transition fittings must not be used in pressure applications, they are designed for an operating pressure of up to 0.5Bar (5m of head), For applications with a greater pressure requirement contact us for a special socket design.
PE Spigot end transitions - are also available by special order. These can be inserted into the sockets of existing DI, CI, Clay, PVC or Concrete pipes, contact us for lead-time.